9 Top 6 Gauge Wire, Sub Panel Solutions
Related photos in this project:
Other recommended ideas:
# 51 Feeding A, Panel Complete Instructions, YouTube - So my advice is a subpanel. The labeling says the largest department circuit breaker you could use is 70a, so ok. Match a 70a breaker in whichever role you could spare, both 1, 2, three-four-5-6, (or four-five if you could discover a double-stuff thqp270). Feed that over to a brand new subpanel. You are welcome to apply some other ge qline panel if you opt for. The panel is rated to support one hundred twenty five amperes, whilst connected to a a hundred and twenty/240 volt three twine machine. Because of this a hundred twenty five amperes can glide thru every of the top bus bars and every predominant lug, with out something melting or catching fire.
As soon as upon a time there was a "rule of six", which said you ought to be capable of shut off all power by way of throwing no more than six breakers. Yours is indeed a "rule of six" panel however with three: the two-pole breakers in positions 1, 2, and the (unnumbered) thriller position underneath 1. In case you have been to turn everything on right now, your load cannot exceed 30,000 watts (30kw). If a load is on for more than 3 hours you need to length the breaker for 80 of the non-stop load. So if this panel have been to most effective serve lighting fixtures, heating, or cooling your max draw may want to simplest be 24,000 watts (24kw) (100a).
Consistent with the panel label, it's miles a 125a rated panel with a 100a sub-segment. The whole panel is rated at 125a, the sub-phase is rated for 100a. The maximum breaker everywhere in the panel may be a 70a. (Except it has. No, simply due to the fact there are x amps of breakers within the panel does now not mean the panel is x or any precise size panel. Indeed, in lots of offerings the sum of the breakers is greater than the panel length certainly because it's miles known that now not the entirety is "on" right now. For instance, electric heating and air con aren't generally operated concurrently.
This need to be a certainly antique container due to the fact i see a 50 amp breaker and a 30 amp breaker i d and predominant breaker at the pinnacle and important breaker on the top. This box ought to be a from the late from the overdue 1960s. Or early seventies however because you're converting the field you would be higher off with a rectangular d. 200 amp box just discovered this put up taylor i respond to it like a country is within the backside. You most effective have a 50 in a 30 which makes makes a total of 80 amps.